Identify Installation Location
FuelCloud uses a wireless signal to communicate with the hardware, and your mobile device needs a line of site to the CloudBox to connect and unlock the pump. Select an installation site that is in visual range, and do not install the CloudBox inside or behind a metal / cement barricade.
Note: For mobile devices to connect to the CloudBox they must be within 150 feet of unobstructed line of site.
Installations must be in accordance with the National Electrical Code (NFPA No. 70) and the Automotive and Marine Service Station Code (NFPA No. 30A). The installer is responsible for investigating and following any applicable local codes.
Access can only be gained by service persons or by users who have been instructed about the reasons for the restrictions applied to the location and about any precautions that shall be taken. Access is through the use of a tool or lock and key, or other means of security, and is controlled by the authority responsible for the location. Seal offs must be used when conduit is exiting an explosion proof zone. (class 1 div 1 or class 1 div 2)
Hazardous Areas - Where not to mount the CloudBox
Note: The CloudBox must be mounted 18" away from a Class 1 div 1 area.
The CloudBox has 4 holes that allow it to be mounted in various setups. Attach the 4 included Mounting Brackets and screws to the CloudBox. Use any available fasteners to mount the CloudBox.