FuelCloud Hardware Power In / Power Out
FuelCloud piggybacks power off of the AC input. Your wiring configuration will depend on whether the pump runs on AC or DC power. For use with DC applications a Class 2 power supply is required for the board’s power.
DC input requires ~12V DC. Attached positive power to DC+ (terminal 3) and ground to DC- (terminal 2) as demonstrated on the graphic to the right.
For output power, attach the load positive load wire to DC+ output (terminal 28) and ground to DC- (terminal 29).
The CloudLink hardware accepts up to 5 pumps or loads. For each additional pump please connect the input and out power on channel 2 through 5.
AC input requires 80-240V AC. Attach Line power to L/DC+ (terminal 3), Neutral to N/DC- (terminal 2), and Earth Ground to (terminal 1).
For output power, attach the load Line wire to the L/DC+ output (terminal 28) and load Neutral to N/DC- (terminal 29).
The CloudLink and CloudBox must be connected together through RS-485 in order to communication. Both hardware units have 3 wiring terminals that must be connected to each other. A, B, and GND on the CloudLink need to be connected to A, B, and GND on the CloudBox.
Article is closed for comments.